Rank: 268 / 726
3 selected articles
Air Conditioning EER, SEER, BTU, BTUH, BTUhr, BTU/hr ...
| Heil® | Temp Star®
- used 0.88 Motor Power Factors
ARI Conditions are: 95ºF-OAT; 80ºF-IDB; 67ºF-IWB or 50%RH | TVA conditions; 95-OAT; 75ºFIDB; 63-IWB or around 50%RH | Try 85ºF-OAT |
Outdoor Ambient Temperature (OAT)
1.5-Ton 18,000 21-F Split Cond. CFM 1400 WATTS 1536 1.5-Ton is from actual published DATA - Only ARI Rating Conditions
1.5-Ton 18,000 @ 95ºF OAT; Indoors 75-IDB;...
Date: 2012-01-27 02:37:56
Related topics : split system air conditioning installation cost / split system air conditioning installation / heating and air conditioning systems problems / air conditioning condenser fan motor replacement / air conditioning system design
Air Conditioning System Sizing for Optimal Efficiency
To find the information below; Use within the pdf search: at least 6" above
Or use down arrow to P-8 & scroll down a-ways...
"If the oil furnace is used in connection with summer air conditioning the evaporator coil must be installed at least 6" above the oil furnace for proper airflow. Distances less than 6" will result in decreased airflow."
Make sure outlet supply takeoffs are NOT blocked by...
Date: 2014-05-12 12:54:45
Related topics : air conditioning system design manual pdf / heating and air conditioning systems problems / air conditioning system design / air conditioning sound effect free / air conditioning system types
Darrell's AC Trouble Shooting Superheat Subcooling Suction ...
Always check both SH & SC for trouble shooting comparison to normal parameters!
Even on service calls where there are cooling problems the ductwork should have a quick Manual D performed.
Take the ESP static pressure & compare to blower graph or chart, also take the FPM duct velocity.
For Room Return Air balancing, i.e., -.01" IWC = approximately -2.48 Pascals, which is a...
Date: 2016-09-01 20:25:32
Related topics : heating and cooling systems problems / air conditioning temperature pressure chart / heating and air conditioning unit problems / heating and air conditioning systems problems / heat and air conditioning problems